UPS scenario ECC scenario NetEco scenario To ensure that the wireless To ensure that the wireless If the LAN switch in the communication signals communication signals are equipment room provides a between the iBOX and the free from interference, the PoE port, no adapter is iBAT are free from interference, distance between the iBOX...
2. Insert the terminal into the iBAT port with force, and ensure that it is securely connected. 3. Attach the iBAT to the top or side of the battery based on the battery installation space. Press the iBAT with your palm for more than 10 seconds to ensure that it is attached firmly and evenly. Installing Hall Effect Sensors •...
Without a neutral wire Cable Label iBOX Port Battery1_HALL1 HALL_1 Battery2_HALL2 HALL_2 Battery3_HALL3 HALL_3 Battery4_HALL4 HALL_4 Cable Label iBOX Port Battery1_HALL1 HALL_1 Battery1_HALL2 HALL_2 Battery2_HALL3 HALL_3 Battery2_HALL4 HALL_4 Battery3_HALL5 HALL_5 Battery3_HALL6 HALL_6 Battery4_HALL7 HALL_7 Battery4_HALL8 HALL_8 For cables with labels Hall+, Hall-, Hall_1, and Hall_2, connect the terminal labeled Hall+ to the positive Hall effect sensor, connect the terminal labeled Hall- to the negative Hall effect sensor, and connect the terminals labeled Hall_1 and Hall_2 to the corresponding ports on the iBOX according to the cable connection sequence.
ECC scenario 1. Remove the battery cabinet panel and knock off the cover on the iBOX indicator hole on the panel. 2. Install the antenna delivered with the iBOX. Ensure that the antenna is perpendicular to the floor. 3. Attach the fastener to the positioning frame of the fixing bracket, press the fastener for more than 10 seconds, and ensure that the fastener is attached firmly and evenly.
Cable Connections and Commissioning (UPS Scenario) Connecting Cables Preparing cables • The PoE port and COM port are PoE Port Pin COM Port Pin connected to RJ45 straight-through cables. Definition Definition • Prepare cables and terminals by yourself. RS485+ RS485- 48V+ RS485+ 48V+...
One UPS is configured with four iBOXs to manage four battery strings respectively Set the iBOX DIP switches, as shown in the figure. The DIP switch addresses of iBOX 1 to iBOX 4 in the management system are 60 to 63.
Logging In to the iBOX WebUI and Setting Parameters 1. Configure the PC and iBOX to be in the same network segment. 2. Use a straight-through cable to connect the PC to the DATA port on the adapter. 3. Open Internet Explorer, choose Tools > Internet Options > Advanced, and ensure that Use TLS 1.1 and Use TLS 1.2 are selected.
Logging In to the UPS WebUI and Setting Parameters 1. Use a straight-through cable to connect the PC to the FE port on the UPS MDU. 2. Enter https://UPS IP address in the address box of Internet Explorer to log in to the UPS WebUI homepage.
Cable Connections and Commissioning (EIC800 or ECC800 Scenario) This document describes the ECC800 as an example. For details about the EIC800, refer to the ECC800 procedure. Connecting Cables The communications cable, with an RJ45 connector, delivered with the BCB box is used to connect the new BIB board, and the cable without an RJ45 connector is used to connect the old BIB board.
Logging In to the ECC800 WebUI and Setting Parameters 1. Use a straight-through cable to connect the PC to the FE port on the ECC800. Default ECC800 settings: 2. Enter https://ECC800 IP address in the address box of • IP address: 192.168.0.10 Internet Explorer to log in to the ECC800 WebUI •...
Old BIB board BIB J1 iBOX BCB 5 OL 6 STA 7 DRV 8 GND New BIB board BIB J1 iBOX BCB 5 OL 6 STA 7 DRV 8 GND Logging In to the iBOX WebUI and Setting Parameters 1. Configure the PC and iBOX to be in the same network segment. 2.
Default iBOX settings: • • User Name: admin IP address: 192.168.0.10 • • Password: Changeme Subnet mask: 255.255.255.0 • Gateway: 192.168.0.1 5. Access the System Settings > Batt. String Config page, and set Batt. String Config parameters according to the following table. Batt.
7. Access the System Settings page, and set the Time, IP Address, Battery Curve, and Parallel Net Join Config parameters according to the following table. System Settings Description Time Set the local time zone, date, and time. Set the IP address, subnet mask, and default gateway of the iBOX. Set IP Address this parameter based on the IP address assigned by the administrator.
Serial Networking • To prevent the iBAT in a different group from connecting to another iBOX, ensure that only one iBOX is under networking at a time. That is, only the RF_Z indicator of this iBOX is blinking at super short intervals. •...
Open the mobile phone app and go to the homepage. Select Stock to access the Stock page. Click + in the upper right corner and choose Ibat Collection. NOTE • You can manually enter SN on the Service Expert app to On the IBAT Scan page, click to collect iBAT SN info.
Appendix Verifying the Installation Check Item Acceptance Criteria Check Result Installation of devices in All devices in the iBattery system are installed □ Passed □ Failed the iBattery system reliably. Labels of cables to the All cables for the iBattery system are POE port, COM port, connected correctly.
iBAT Indicator Color Meaning Status Description Power consumption is low. The iBAT is not powered on. Blinking at short Green RUN The networking has started but not completed. intervals Blinking at long The networking succeeds. intervals The iBAT is not faulty. ...
Scan here for technical support (carrier): Huawei App Store Scan here for more documents: Support-E Support WeChat You can also log in to Huawei technical support website: http://support.huawei.com/enterprise http://support.huawei.com Huawei Technologies Co., Ltd. Huawei Industrial Base, Bantian, Longgang Shenzhen 518129 People's Republic of China...