KEY TO SYMBOLS AND SAFETY INSTRUCTIONS Flue systems must not be modified in any way other than as described in KEY TO SYMBOLS AND SAFETY the fitting instructions. Any misuse or unauthorised modifications to the appliance, flue or associated components and systems could invalidate INSTRUCTIONS the warranty.
PRODUCT INFORMATION PRODUCT INFORMATION PRE-INSTALLATION BALANCED LOW LEVEL DISCHARGE FLUE BALANCED LOW LEVEL DISCHARGE FLUE OPTIONS COMPONENTS NOTICE: ▶ It is recommended that the flue terminal faces away from walls to minimise wetting ▶ Flue gases have a tendency to plume and in certain weather conditions a white plume of condensate will be produced.
INSTALLATION INSTALLATION NOTICE: 2&3 ▶ Ensure all seals are in good condition and seated properly. ▶ To ease assembly of the flue components, lightly grease the seals with the solvent free grease supplied. ▶ A terminal guard must be fitted if the terminal is 2 m or less above a surface that is accessible by people.
INSTALLATION SIDE FLUE OPTION: DANESMOOR (2013) AND HEATSLAVE II To use the right hand or left hand flue options a 90° swept flue elbow is required (part no. 7 716 190 034) Lightly grease the 90° flue elbow seals with the solvent free grease.
INSTALLATION SIDE FLUE OPTION: CAMRAY AND HEATSLAVE To use the right hand or left hand flue options a 90° swept flue elbow is required (part no. 7 716 190 034) Lightly grease the 90° flue elbow seals with the solvent free grease supplied.
INSTALLATION ▶ Push the air inlet inner section through the side panel opening into the ALL FLUE OPTIONS, FINAL ASSEMBLY air box until it meets the stops  on the clamp assembly ▶ Lightly grease the flue pipe seal with the solvent free grease supplied. ▶...
INSTALLATION TERMINAL GUARD ▶ To fit the terminal guard  not supplied: Hold the terminal guard  in place and secure with the four screws  removed from the air box earlier. 6720807912-19.1Wo Fig. 19 Terminal guard Screws 6 720 807 912 (2015/10)