AC Smart II TABLE OF CONTENTS Safety precautions ......................3 Introduction of AC Smart II....................7 AC Smart II characteristics ....................7 AC Smart II exterior ......................8 AC Smart II component .....................9 AC Smart II product specification ..................9 ABOUT AC Smart II ......................10 Logging on to AC Smart II ....................10 AC Smart II screen composition ..................11 About control/monitoring menu..................13...
Safety Precautions Safety Precautions To prevent injury to the user or other people and property damage, the following instructions must be followed. ■ Incorrect operation due to ignoring instruction will cause harm or damage. The seriousness is classified by the following indications. WARNING This symbol indicates the possibility of death or serious injury.
Safety Precautions While re-installing the Do not use the power cord Do not disjoint randomly or established product, notify near Flammable gas or repair and remodel the the service center or combustibles, such as product. establishment specialty gasoline, benzene, thinner, store etc.
Safety Precautions Do not put firearms near Do not put an electric heater Do not spill water inside product. or conductor near to the product. product. • It can cause fire. • It can cause fire and • It can cause electric electric shock.
Safety Precautions CAUTION ■ During usage Clean by soft hands Use touch screen with a Do not place any live part using a cleaning material pen that product offers. on the surface having like a soft cloth. water. • It can result in fire and •...
Introduction of AC Smart II Introduction of AC Smart II AC Smart II is a central controller that can manage maximum of 64 air condition indoor units individually or as a group. Also when you connect the AC Smart II expansion kit (PQCSE440U0), you can expand up to 128 units.
Introduction of AC Smart II Web server and E-mail notification function AC Smart II provides a web server function for the administrator to control the air conditioner by accessing the AC Smart II remotely through the network. Also it provides the E-mail notification function to notify the error to the administrator located remotely via E-mail.
Introduction of AC Smart II AC Smart II Component The components of AC Smart II are as follows inside the box. Open the box of AC Smart II and check whether all components are included. AC Smart Power adapter Quick Guide Manual CD Power cord AC Smart II product specification...
About AC Smart II About AC Smart II This chapter describes how to log in to AC Smart II and the functional menu of AC Smart II. Logging on AC Smart II When you turn on the power of AC Smart II, the following log in screen will be displayed. You can log in as installation expert, administrator and general user to AC Smart II.
About AC Smart II About AC Smart II screen composition When you log in to AC Smart II, the following screen will be displayed. Log out button AC Smart II menu Log out button When you press the log out button, you will log out from AC Smart II and return to the log in screen. AC Smart II Menu Function provided in AC Smart II is displayed.
About AC Smart II When the user selects a specific function, the execution screen of the applicable function will be displayed. The following is an example of the Control/Monitoring menu. Log out button Home button Function execution screen Message window Home button When you press the Home button, it will switch to the menu selection screen of AC Smart II.
About AC Smart II About control/monitoring menu Control/Monitoring menu is the menu to easily manage various units (Indoor units, ventilator, AWHP) in one unit that can be commonly controlled. You can monitor or control the status information from Control/Monitoring menu in Zone, Group or Unit. Control/Monitoring menu screen is composed as follows.
About AC Smart II ■ Zone, group, and unit status display Status display of zone, group and unit Control/Monitoring menu displays the status of Zone, Group or Unit (Indoor unit, ventilator) through the following icons. When you set the information display method to ʻIcon”, it is displayed as follows. Icon Status Zone...
About AC Smart II Unit operating mode display AC Smart II displays the operating mode of each unit with the following icon. When you set the information display method to ʻIconʼ, it is displayed as follows. Unit type Icon Description Icon Description Icon...
About AC Smart II Unit alarm display AC Smart II displays the current alarm with the following icon. In the following example, the indoor unit is used. When you set the information display method to ʻIcon”, it is displayed as follows. Alarm Description Alarm...
About AC Smart II ■ Zone, group and unit monitoring and control Monitoring information display of zone and group There is the ʻMonitoringʼ tab on the bottom of the Control/Monitoring menu. Monitoring tab displays the detail information of the selected Zone, Group or Unit. The monitoring information of the Zone or Group is differently displayed as the monitoring information of the Unit.
About AC Smart II In the monitoring tab of the unit, you can see the more detailed information of the unit. When you press the [Detail] button, the monitoring window showing the detail information of the unit will be displayed as shown in the left picture. <Indoor unit condition screen>...
About AC Smart II Run/Stop Set the operating ventilator Ventilator mode, fan level and operation. lock function. Display the detail control screen so Apply current that the ventilator can be setting. controlled in detail. On/Off device Run/Stop On/Off device operation. Apply current setting.
About AC Smart II About schedule menu Schedule is the function to execute the operation at a preset time by setting the operation of the unit beforehand. You can set the schedule of the unit in Group from the schedule menu. In AC Smart II, you can create a schedule group to commonly apply the schedule.
About AC Smart II ■ Schedule setting method This chapter shows how you can set the schedule assuming that you have just installed AC Smart II. Create schedule group In order to create the schedule after installing AC Smart II for the first time, you must first create a schedule group.
About AC Smart II . Press the [Save] button to save the current setting. When the setting is saved, it will return to the previous screen. Create weekly schedule pattern When the schedule group is created, you must set the weekly schedule pattern. .
About AC Smart II . Select ʻAdd schedule patternʼ and click on the [Next] button. . Enter the weekly schedule pattern, and click on the [Next] button. . Select the time to operate the device from ʻSelect timeʼ or ʻSchedule timeʼ. And set the device operation from the ʻControl settingʼ...
About AC Smart II . Message saying that schedule pattern edit is complete is displayed. Click on the [OK] button to complete the edit. Information: Apply daily schedule pattern and daily schedule repeat While creating/editing the weekly schedule pattern, you can apply the daily schedule pattern.
About AC Smart II Apply schedule You can apply the schedule after integrating the information of schedule group, schedule pattern and period. To apply the schedule, proceed as follows. . To apply the schedule, press the [Schedule wizard] button . Schedule wizard screen is displayed. Select ʻAdd/Edit scheduleʼ, and select the schedule group to apply the schedule.
About AC Smart II . When you click on the button, the calendar will be displayed. Use the calendar to select the period (Start date, End date) to apply the schedule. After entering the period, click on the [Next] button. .
Introduzione ad AC Smart II Introduzione ad AC Smart II AC Smart II è un controller centrale in grado di gestire fino a 64 condizionatori interni singolarmente o in gruppo. Inoltre, quando si collega il kit di estensione AC Smart II, è possibile controllare fino a 128 unità...