Necessary Tools for Installation
Hole core drill
Spanner(17,19 and 26mm)
Gas leakage detector or
Selection of Installation Place
Place, robust not causing vibration, where the body can be
Place, not affected by heat or steam generated in the vicinity,
where inlet and outlet of the unit are not disturbed.
Place, possible to drain easily, where piping can be conne-
cted with the outdoor unit.
Place, where cold air can be spread in a room entirely.
Place, nearby a power receptacle, with enough space around.
Place where the distance of more than lm from televisions,
radios, wireless apparatuses and fluorescent lamps can be
In the case of fixing the remote controller on a wall, place
where the indoor unit can receive signals when the fluore-
scent lamps in the room are lightened.
The models adopt HFC free refrigerant R410A
more than 15 cm
The distance between the indoor unit and the floor should be more than 2m.
Please be subject to the actual product purchased,the above picture is just for your reference.
Indoor Unit Installation
Drawing for the installation of indoor units
Before inserting power into receptacle, check the voltage without
The power supply is the same as the corresponding nameplate.
Install an exclusive branch circuit of the power.
A receptacle shall be set up in a distance where the power cable
can be reached.Do not extend the cable by cutting it.
Remote controller (1)
R-03 dry battery (2)
Mounting plate (1)
FOR 09K 12K
Attention must be paid to
the rising up of drain hose
more than 10cm
Drain hose (1)
Plastic cap (4)
Ø4X25 Screw (4)
Air purifying filter(Optional) (1)
Selection of Pipe
Arrangement of piping