step by step Guide To slim Duct Unit Installation
There are three methods to connect the wired controller to
the indoor units.
A. One wired controller controls one indoor unit; the indoor
unit connects with the wired controller through a 3 conductor
B. One wired controller can control up to 16 sets of indoor
units (max); A 3 conductor shielded cable must connect
the wired controller and the master unit (the indoor unit
connected to the wire controller directly). The others connect
to the master unit through a 2 conductor shielded cable.
C. Two wired controllers control one indoor unit. The wired
controller that connects with the indoor unit is called the
master controller, the other is called the slave controller. The
master wired controller and the indoor unit (as well as the
master controller and the slave controller) are all connected
through 3 conductor shielded cables.
0~100 ft (0~30m)
100~200 ft (30~60m)
200~300 ft (0~90m)
300-400 ft (90~120m)
400~500 ft (120~150m)
Wired Controller Wiring Instructions
Dimension of Wiring
1. Put communication wire through the hole in the back cover
2. Mount the back cover in the desired location, making sure
not to pinch the communication wire. Then connect the com-
munication wire to CON1 port of the wired controller. Replace
the cover onto the unit to complete the installation.