United States Environmental Protection Agency (EPA). For service or repairs to boiler, call your heating contractor. When seeking information on boiler, provide Boiler Model Number and Serial Number as shown on Rating Label. Boiler Model Number...
8. FOR OPTIMUM PERFORMANCE AND SERVICEABILITY FROM THIS BOILER ADHERE TO THE FOLLOWING RECOMMENDATIONS: A. DO NOT TAMPER WITH THE BOILER OR CONTROLS. Retain your contractor or a competent serviceman to assure that the boiler is properly adjusted and maintained.
Before starting to in stall this oil bo iler, read these in structio ns carefu lly. Keep instruction s in legible condition and po sted n ear oil boiler fo r reference by owner an d service technician . TABLE OF CONTENTS General Information ...
NOTE 1: Listed clearances comply with American National Standard ANSI/NFPA 31, Installation of Oil Burning Equipment. NOTE 2: V7 Series boilers can be installed in rooms with clearances from combustible material as listed above. Listed clearances cannot be reduced for alcove or closet installations.
SECTION II: KNOCKDOWN BOILER ASSEMBLY A. REMOVAL OF BARE BOILER FROM SKID 1. Boiler is secured to base with 4 bolts, 2 on front and 2 on rear, see Figure 2. Remove all bolts. 2. Tilt boiler to right and to rear. Using right rear leg as pivot, rotate boiler 90°...
Secure with #8 x ½” long sheet metal screws. 5. Install jacket top panel. Place jacket top panel on boiler and secure to front, rear and left side panels with #8 x ½” long sheet metal screws. 6. Install jacket lower right side panel. Align right side panel mounting holes with front and rear panel holes.
3. Engage bottom slot on burner mounting plate with matching bolt in bottom tapping of front section. Align mounting holes and fasten the mounting plate to the boiler sections with (5) five 5/16” bolts and washers removed in step 8a. Fully tighten all bolts.
“G” (see Figure 4) is used for standard return on water boilers). 5. If CIRCULATOR (not supplied with boiler) is to be mounted directly to 1½" boiler return tapping "G", use the piping arrangements outlined in steps a. thru e.
B. REMOVAL OF BOILER FROM SKID TS-39-26-A Fig. 7 1. Boiler is secured to base with 4 bolts, 2 on left side and 2 on right side, see Figure 7. Remove all bolts. 2. Tilt boiler to right and to rear. Using right rear leg as pivot, rotate boiler 90°...
CAUTION Oxygen contamination of boiler water will cause corrosion of iron and steel boiler components, and can lead to boiler failure. Burnham's standard warranty does not cover problems caused by oxygen contamination of boiler water. There are many possible causes of oxygen contamina- tion such as: 1.
Most homes have a chimney appropriate for the fuel and the era in which the home was built. That may have been a coal fired or an inefficient oil fired boiler built into a home without insulation or storm windows.
That probably means that the stack temperature from the new boiler will be lower than that from the old boiler and with less room air being drawn up the chimney to dilute the stack gases. The combination of a large uninsulated...
Figure 15 IMPORTANT Single-pipe installations must be absolutely airtight or leaks or loss of prime may result. Bleed line and fuel unit completely. Figure 16 TABLE 4: SINGLE-STAGE UNITS (3450 RPM) - TWO-PIPE SYSTEMS Manimum Length of Tubing "H" + "R" (See Figure 16) Lift "H"...
The low water cut off will shut down the burner if the water level in the boiler drops too low. The control resets and restarts the burner with a call for heat a few seconds after the water is returned to its normal level.
If burner ignites within approximately 45 seconds and the cad cell sees flame the burner will continue to operate until the call for heat is satisfied. The circulator will also operate when the thermostat calls for heat if the boiler water temperature is up to the setting of the low limit in the L8124C control.
Before opening swing door, turn off service switch to boiler to prevent accidental firing of burner outside the combustion chamber. Be sure to tighten swing door fastener completely when service is completed.
For optional burners, Riello R40 and Carlin EZ-1HP and 102CRD-3, consult Table 6 at the rear of this manual for specifications, the instruction booklet shipped with the burner, and the appropriate Supplemental Instructions shipped w ith the boiler: Supplemental Instructions for: F.
After service is complete, be sure to fasten down the ignitor. 7. FLAME FAILURE The V7 boiler controls operate the burner automatically. If for unknown reasons the burner ceases to fire and the reset button on the primary control has tripped, the burner has experienced ignition failure.
Follow these steps to inspect, clean and/or replace the probe: a. Turn off electric service to the boiler. b. Drain boiler water to a level below the tapping for the probe. c. Disconnect wiring connections between the low water cutoff control and the probe.
Add boiler water treatment compound as needed (refer to paragraph N.). o. Restore electric service to the boiler. p. Fire burner to bring the water in the boiler to a boil to drive off free oxygen. q. WARNING — BEFORE RETURNING BOILER TO SERVICE: Follow the low water cutoff check out procedure in step L.4..
With this lower level of protection, care must be exercised to eliminate all of the free oxygen in the system. e. Boiler is now ready to be put into service. O. HINTS ON COMBUSTION 1. NOZZLES — Although the nozzle is a relatively inexpensive device, its function is critical to the successful operation of the oil burner.
3. With steam boilers, at end of season add sufficient water to fill boiler to top of water column and leave it that way until fall when water should be drained again to proper level. If at this time boiler water is dirty, drain water, flush out boiler, and refill with clean water to prescribed water level.
, per sona l injury or los s of lif e if ignor ed. B ef ore ope nin g s wing d oor, tu rn of f se rvice sw it ch to boiler to prev en t a cc ide nta l firing of b urne r out si de the co mbus tion c ham ber.
The boiler must be connected to an approved chimney in good condition. Serious property damage could result if the boiler is connected to a dirty or inadequate chimney. The interior of the chimney flue must be inspected and cleaned before the start of the heating season and should be inspected periodically throughout the heating season for any obstructions.
All V7 Series Repair Parts may be obtained through your local Burnham Wholesale distributor. Should you require assistance in locating a Burnham Distributor in your area, or have questions regarding the availability of Burnham products or repair parts, please contact your Burnham Regional Sales Office as listed below.
Item Description BARE BOILER ASSEMBLY (See Page 32 for Illustration) Front Section (Non-Htr.), Machined Water Front Section (Non-Htr.), Machined Water Front Section (Non-Htr.), Machined Steam Front Section w/Htr. Opening, Machined Water Front Section w/Htr. Opening, Machined Steam Center Section Center Section Narrow Back Section (Non-Htr.), Machined...
Item No. Description V713 and V714 Flush Jacket Components - Items 1 thru 6 Include Insulation As Part of Assembly Jacket Front Panel Assembly Jacket Rear Panel Assembly Jacket Left Side/Top Panel Assembly Jacket Top Panel Assembly Jacket Lower Right Side Panel Assembly Jacket Upper Right Side Access Panel Assembly without Heater Opening (WB Only) Jacket Upper Right Side Access Panel Assembly with Heater Opening (WBT Only)
BECKETT OIL BURNER PART NOS. FOR V7 SERIES BOILERS NOTE: When ordering parts always give the serial and model numbers shown on the boiler and burner. Also provide the name of the part(s) and part number as listed below. Boiler Model...