Multi V™ Ducted (High Static)
Btu/h Indoor Unit
Total Cooling Capacity (Btu/h)
Heating Capacity (Btu/h)
Power Input¹ (W)
Cooling Nominal Test Conditions:
80°F DB/67°F WB
Power Supply (V/Hz/Ø)
Rated Amps (A)
Liquid Line (in, OD)
Vapor Line (in, OD)
Condensate Line (in,OD)
Factory Installed Pump²
(Heat Recovery only)
•Auto opera on
•Dual thermistor control
Wireless Handheld Remote Controller (PQWRHDF0)
7‐Day Programmable Controller (PQRCUSA)
Simple Controller with Mode (PQRCUCS0C)
Simple Controller without Mode (PQRCFCS0C)
Dry Contact Unit (PQDSB1, PQDSBC)
Wall Mounted Temperature Sensor (PQRSTA0)
LG Electronics USA, Inc. 1000 Sylvan Ave, Englewood Cliffs, NJ 07632/www.lg‐vrf.com
For continual product development, LG reserves the right to change specifications without notice.
Heating Nominal Test Conditions:
47°F DB/43°F WB
•Self diagnos cs
•So dry (dehumidiﬁca on)
•Fan speed control
Entering Mixed Air:
Cooling Max⁴ (°F WB)
Heating Min (°F DB)
Sound Pressure⁵ dB(A) (H/M/L)
Net Unit Weight (lbs)
Shipping Weight (lbs)
Airflow Rate H/M/L (CFM)
External Static Pressure⁶ (in wg)
•Limited Warranty with LG Cer ﬁed Installa on
•Two Year Functional Parts Warranty
1.The Power Input is rated at high speed.
2.Maximum li is 27 in from bo om of unit.
3.Requires a 7‐Day programmable controller.
4.See Engineering Manual for sensible and latent capaci es.
5.Sound Pressure levels are tested in an anechoic chamber under ISO Standard 1996.
6.Factory set as standard.
7.All communica on cable to be minimum 18 AWG, 2‐conductor, stranded, shielded and must
comply with applicable local and national code.
8.Power wiring cable size must comply with the applicable local and na onal code.
9.This unit comes with a dry nitrogen charge.
10.This data is rated 0 above sea level, with 25 of refrigerant line per indoor unit and a 0
level difference between outdoor and indoor units. All capacities are net with a combination ratio
between 95 – 105%.
11.Must follow installa on instruc ons in the applicable LG installa on manual.
Brushless Digitally Controlled/Direct
Page 1 of 2