13 SEER WHEN THIS APPLIANCE IS INSTALLED IN AN ENCLOSED AREA, SUCH AS A GARAGE OR UTILITY ROOM, WITH ANY CARBON MONOXIDE PRODUCING DEVICES (i.e. AUTOMOBILE, SPACE HEATER, WATER HEATER,ETC.) INSURE THAT THE ENCLOSED AREA IS PROPERLY VENTILATED. CARBON MONOXIDE (REFERED TO AS CO) CAN CAUSE PERSONAL INJURY OR DEATH FAILURE TO FOLLOW THESE INSTRUCTIONS, LOCAL CODES OR NATIONAL CODES MAY CAUSE FIRE, EXPLOSION, ELECTRICAL SHOCK, PERSONAL...
TOPIC General Physical dimensions Replacement Parts Source Installation Requirements Air Flow Orientation Horizontal Left-Hand Instructions Refrigerant Tubing Condensate Removal Electrical Connections Thermostat Wiring Orifice Change Circulating Air Duct Blower Performance Start-up Regular Maintenance Model Number Explanation The United States Environmental Protection Agency (EPA) has issued various regulations regarding the introduction and disposal of refrigerants introduced into this unit.Failure to follow these regulations may harm the environment and can lead to the imposition of substantial fines.
PHYSICAL DIMENSIONS 1" [2.54 cm] 3.3" [8.3 cm] 2.4" [ 6 cm] 1.2" [3 cm] INLET FRONT VIEW PRIMARY & SECONDARY CONDENSATE DRAINS- UPFLOW 3/4" NPT-FEMALE 46.7 18.3 [118.7cm] [55.9cm] [46.4cm] [50.0cm] [25.4cm] [36.8cm] [30.3cm] [43.5cm] [50.3cm] [8.6cm] of 2 Ton PLASTIC BREAKER COVER SUCTION LINE PRIMARY &...
of 3 Ton PHYSICAL DIMENSIONS INLET BOTTOM SIDE VIEW PLASTIC BREAKER COVER ELECTRICAL POWER SUPPLY SUCTION LINE LIQUID LINE LOW VOLT SUPPLY ELECTRICAL POWER SUPPLY...
of 4,5 Ton PHYSICAL DIMENSIONS INLET BOTTOM SIDE VIEW PLASTIC BREAKER COVER ELECTRICAL POWER SUPPLY SUCTION LINE LIQUID LINE LOW VOLT SUPPLY ELECTRICAL POWER SUPPLY...
REPLACEMENT PARTS SOURCE Replacement parts are available through local distributors.When ordering replacement parts, give the COMPLETE model and serial numbers shown on the rating plate. INSTALLATION REQUIREMENTS Before installing this appliance insure that it is properly sized and adequate power is available. This appliance can be installed in the vertical or right horizontal position without modification.
AIR FLOW ORIENTATION *Upflow Discharge *Air Handler is factory ready for Upflow & Horizontal Right Discharge Application for 3*4*5 as shown. *Air Handler is factory ready for Upflow & Horizontal Left Discharge Application for 2 as shown. *Horizontal Right Discharge Tube and Drain conn.
HORIZONTAL LEFT-HAND INSTRUCTIONS Important: Read instructions below carefully. Plastic Drain cover WARNING: If incorrect knockouts are removed, flooding will occur. 5) Reinstall in the Airhandler, the "A" coil pan assembly with the horizontal drain pan on the left-hand side. Note: Push the assembly completely to the rear of the cavity and assure it slips into channel bracket at the rear of the cavity.
REFRIGERANT TUBING Refrigerant tubing should be installed as to avoid undue stress. They must be supported or routed to avoid strain or vibration. To avoid damage that can be caused by condensate, insulate the suction tube with a closed cell insulation with the seams sealed. The insulation should terminate at the tubing entrance to the air handler.
ELECTRICAL CONNECTIONS The required electrical power supply information is located on the series and rating plate on the exterior of the unit. Wiring selection must be in accordance with local codes, or in absence of local code, the National Electrical Code. A disconnect means should be installed within sight of the unit, when required by code.
THERMOSTAT WIRING For Thermostat Control Environment-temperature and Air Conditioning open/stop, the wiring diagram as shown diagram 1. Thermostat can be mechanical type or programmable type. Note: Thermostat C : COM. R : AC24V Y : COMPRESSOR G : FAN O : 4 -WAY VALUE For detailed Thermostat, please connect corresponding terminal according to above control specification.
For Thermostat Control Environment-temperature and Air Conditioning open/stop, the wiring diagram as shown diagram 4. Thermostat can be mechanical type or programmable type. Note: Thermostat C: COM. R : AC24V Y : COMPRESSOR G : FAN For detailed Thermostat, please connect corresponding terminal according to above control specification.
ORIFICE CHANGE The restrictor (orifice) included in this unit match the comparable capacity of the outdoor unit. If the indoor unit is greater in capacity than the outdoor condenser, the orifice must be changed to match the outdoor unit capacity. The restrictor (orifice) should be replaced before any tubing connections are made.
BLOWER PERFORMANCE CFM versus Static Pressure (inches of water column dry coil w/ filter) 4% reduction for wet coil. Static Pressure Model High 2 Ton Middle High ------ 1240 3 Ton ------ 1125 High 4 Ton ------ ------ High 5 Ton ------ ------ ------ High...
START-UP Prior to initial start-up insure that all electrical connections are properly sized and tightened. All panels must be in place and secured. Tubing should be leak free. Unit should be elevated, trapped and pitched to allow for drainage. Low voltage wiring is connected. Auxiliary drain is installed, when necessary, and pitched to allow for drainage.