Summary of Contents for Honeywell GENT VSINTM-PCB-UPG
Installation Replacement Interface Board by Honeywell (VSINTM-PCB-UPG) for 34440 Interface Spare Parts These instructions cover the installation of a Replacement Mains Interface Board on a carrier Fuse 3.15A AS Ceramic (VSINTM-PCB-UPG) into a legacy 34440 Mains (20mm x 5mm) powered interface unit.
Installation Replacement Mains Interface Board Removal Use the [Test/Eng] menu at the control panel and [Stop] the loop circuit on which the 34440 Mains powered interface unit reside. & Before removal of the 34440 Mains Interface Board from the 34440 Mains powered interface unit, first completely isolate the mains supply to the unit.
Replacement Mains Interface Board Installation Replacement The external mains cable should be rewired so that it enters the enclosure above the Mains terminal block on the Replacement Mains Interface Board, this ensures there is segregation between mains and extra low voltage cables. Also, each unused cable entry point must be fitted with a plastic bung. Fit the Replacement Mains Interface Board on a carrier into the enclosure using the screws supplied.
Do not burn. Gent by Honeywell reserves the right to revise this publication from time to time and make changes to the content hereof without obligation to notify any person of such revisions of changes.