Haier flat panel solar collector Installation manual Model： PGT2.0-2 Prepared by： Qingdao economic and technology development zone Haier water heater company Prepared date： 2009.02.18...
CONTENTS Ⅰ、Haier solar panel performance parameter 1、technical specification 2、pressure falloff curve 3、installation angle 4、solar panel dimension Ⅱ、heat-conducting medium for solar heating system Ⅲ、lightning conductor Ⅳ、solar panel installation manual A、installation method for pitched roof 1、tile roof 2、color steel roof B、installation method for flat roof C、installation method for vertical wall...
Model Exterior size (mm) area (m (kg) (kg) PGT2.0-2 2000*1020*84 Maximum loadability of the plate collector: without being damaged by the test pressure of 1.2MPa and the working pressure is 0.15～0.2MPa. 2. Pressure drop graph of one collector Flow/pressure graph of one plate heat collector 3.07...
3. The angle for mounting the collector How to select the tilt angle α for mounting the collector: When the solar system is applicable in four seasons: α=β When the solar system is used mainly in summer: α=β-10 ...
The 16 holes (φ9) above are prepared for fixing the collector. II. The introduction of the relevant heat conducting media of the plate heat collecting system It is the twice (secondary) circulation system that must be selected for the area where icing is possible. The antifreeze shall be used in the heat conducting medium and propylene glycol is recommended to be used as the antifreeze (It is forbidden to use the once (primary) circulation system in the area where icing is possible);...
Open the automatic exhaust valve first and close the valve at the inlet of the expansion tank. Connect the outlet of the liquid filling pump to valve 1 and ensure that the water flows in the same directions for mounting check valve. Connect the suction nozzle of the pump and water-return pipe to the liquid filling tank.
III. Introduction of the lightning arrestor Since collectors are mounted on roofs, they are vulnerable to lightning strikes. Therefore, they shall be mounted in the area which is well protected against lightning. If there isn’t any lightning arrestor, to protect the plate collector, a lightning rod or grounding line is required.
Notes: 1. If the building has a lightning arrestor, it shall be made sure by the local professional if the collector is well protected by the lightning arrestor. 2. If the collector can be protected, the frame mounted on-site shall be connected to the existing lightning belt with equipotential bonding.
(I) There are two ways to mount the collector on a sloped roof, depending on the roof style: How to mount it on a tile roof: How to mount it on a color steel roof: 1. How to mount it on a tile roof: （1）...
3:Collector connector （There is a wrong mark in the 1:Channel steel 2:Collector fixing hook drawing） 4:Wood screw 5:Angle iron piece 6:Bolt 7:Nut Step 1: Remove the tile from the place where the plate collector shall be mounted and fixed. Step 2: Prepare angle iron pieces 5 (L40*70*120*4); fix them onto the roof beam with wood screw 4 after drilling its side wall;...
固定螺栓 M8 16 平板集热器 Set bolt M8*16 Plate heat collector Prepared expansion bolt 预留膨胀螺栓M12 挂瓦条 Batten 集数器连接件 Heat collector connector 密封油膏 Sealing grease 2:Collector fixing hook 3:Collector connector （There is a wrong mark in the drawing） 1:Channel steel 4:Prepared bolt 5:Bolt 6:Nut Step 1: Build M12 bolt 4 onto roof with concrete;...
Step 2: Prepare the collector connector 3, drill holes on its bottom and fix it with bolt 4. Step 3: Fix the drilled channel steel 1 and collector connector 3 with bolt 5. （2）Put tile back to its original place when the collector connector is assembled. （3）Fix the channel steel with collector connector with bolt 5, mount the collector fixing hook 2 onto the lower channel steel, cushion them with rubber pad 4, mount plate collector 1 onto it, hook the lower edge of the plate collector 1, fix the upper edge with the fixing hole on the outer frame, and connect plate collector and the fixed...
2. How to mount it onto color steel roof: 现场钻孔 Drilling hole on-site...
1:Channel steel connector 2:Nut 3：Gasket 4:Rubber gasket 5:Collector fixing Bolt 6:Spring shim 7:Nut 8:Color steel plate 9:C steel Step 1:Drill holes on the color steel and C steel; Step 2:Insert the collector fixing bolt into the holes drilled; assemble nut 7 and spring shim 6 in order and tighten them;...
II. How to mount the collector on flat roof 1. How to prefabricate the foundation of the collector Select a proper foundation for the collector according to the actual roof condition, which may be a field casting concrete frusta or concrete brick. No matter which way is taken, the top of the foundation for the collector shall be leveled.
1: Bottom rod of the support 2: Vertical rod of the support 3: Tilted rod of the support 4 and 7: Bolt 5 and 8: Nut 6: Channel steel 9:Collector fixing hook Step 1: Fix angle iron 1 onto the concrete foundation with expansion bolt; Step 2: Make angle iron 2 and 3 a triangle frame with bolt 4 and nut 5;...
3. How to mount the plate collector 1: Plate collector 2:Collector fixing hook 3:Channel steel 4:Rubber pad...
Step 1: Fix the collector onto the assembled support, clutch the lower edge of the collector with the collector fixing hook; the upper edge of the collector shall be fixed through the fixing hole on its outer frame. Connect the plate collector to the fixed channel steel with a bolt.
III. How to mount the collector on an external wall The requirement to the wall body for mounting the collector on external wall: The loadability of the external wall shall be 2 times the total mass of the collector loaded fully with water and there shouldn’t be any deformation, crack or chip on the wall body.
1: Expansion bolt 2: Channel steel 3: Bolt 4、6: Nut 5: Plate collector 7: Collector fixing hook Step 1: Drill 3 holes on the external wall and insert the expansion bolt 1 into the holes; Step 2: After drilling holes on the channel steel 2, fix the channel steel 2 and collector fixing hook 7 onto the external wall with expansion bolt 1 and nut 4.
5 号槽钢 M8 expansion bolt #5 Channel steel M8 expansion bolt M8 膨胀螺栓 M8 螺栓 M8 bolt 平板集热器 Plate heat collector 平板集热器 Plate heat collector M8 螺栓 M8 bolt 5 号槽钢 #5 Channel steel M8 膨胀螺栓 M8 expansion bolt 2. When the plate collector is mounted to the external wall not vertically...
1: Support frame 2: Front support 3: Support connecting rod 4: Expansion bolt 5:Bolt 6: Plate collector 7: Bolt...
Step 1: Make support 1, 2 and 3 of the collector with angle steel as per the drawing above and assemble support 1, 2 and 3 with bolt 5; tighten and fix them; Step 2: Drill holes on the external wall and insert expansion bolt 4 into the holes; Step 3: Fix the support which has been assembled in step 1 onto the external wall;...
V. Introduction of how to mount pipes for the plate collector 1. How to connect two plate collectors There are two ways to connect two plate collectors next to each other. Such mounting ways can ensure that the pipe distance in the system is equal and can shorten the hot water circulation pile, which can reduce the thermal loss from the pipe and increase the heat collecting efficiency of the solar system.
The 2 Method： Name Specification Connect one end to the copper pipe（￠ 卡套 Stopper 2 sets 22） and the other end is a G3/4 stopper Plate collector 1998*1024*80（mm） Connect one end to the copper pipe 卡套 connector （￠22） and another end interface is 6 sets G1/2 male thread 200mm long;...
2. How to connect 3 plate collectors： To mount 3 plate collectors, the pipelines can be adjusted left and right according to the actual site conditions. The pipes and fittings shall be mounted in the same way for mounting two collectors above. 3.
The 2 Method: If the mounting area is limited, the collector array may be mounted in the following way. For this kind of array of collectors, 4 plate collectors shall be connected in parallel too and they are not put in one row. The pipes and fittings shall be mounted in the same way as mounting two collectors above.
The 3 Method: The kind of array of the collector needs less mounting area, but first two collectors shall be connected in parallel and then assemble two sets of the connected collectors in parallel too. The pipes and fittings shall be mounted in the same way for mounting two collectors above.
The 4 Method: The kind of array of the collector needs less mounting area. To connect the collectors, connect two of them in parallel first and then assemble two sets of the connected collectors in parallel. The pipes and fittings shall be mounted in the same way for mounting the collectors above.