This manual contains proprietary and confidential information of C&C Power, Inc., and has been prepared for the use of Mitsubishi Electric Power Products, Inc., for use in conjunction with equipment provided by C&C Power, Inc. unauthorized reproduction, in whole or in part, without written permission of C&C Power, Inc., is prohibited.
ABLE OF ONTENTS 1. Important Information About This Manual ................. 6 1.1 Manual Symbols ........................6 2. Introduction: ..........................7 3. Safety Precautions ........................8 4. Inspection Upon Receipt of Goods .................... 10 4.1 General ..........................10 4.2 Visible Damage ........................10 4.3 Concealed Damage ......................
BC29 B ATTERY ABINET 1. I MPORTANT NFORMATION BOUT ANUAL SAVE THESE INSTRUCTIONS! This manual contains important information that is needed during the installation and maintenance of the system. 1.1 M ANUAL YMBOLS Warning: Indicates information provided to protect the user against personal injury and/or safety hazards.
BC29 B ATTERY ABINET 2. I NTRODUCTION The C&C Power family would like to thank you for choosing a C&C Power Inc. product for your equipment needs. We know there are a lot of choices in the industry and we appreciate the opportunity to supply each of our customers with the highest quality power products manufactured in the United States today.
BC29 B ATTERY ABINET 3. S AFETY RECAUTIONS Before installing or maintaining this system, it is extremely important to read this manual and be sure that all system drawings and schematics are reviewed and clearly understood. If there are any questions concerning this manual or any of the installation or maintenance procedures and/or requirements please contact a C&C Power representative before proceeding.
BC29 B ATTERY ABINET To avoid personal injury including electrical shock, severe burns and possible death, all jewelry including bracelets, rings and watches must be removed prior to installing or servicing this system. Do not open or mutilate batteries. Opened or severely damaged batteries can release toxic electrolyte which is harmful to the skin and eyes.
BC29 B ATTERY ABINET 4. I NSPECTION ECEIPT OF OODS 4.1 G ENERAL Special precautions and care have been taken to ensure the system arrives safe and undamaged. However, upon receipt, you should inspect the entire shipment, including the crate and any boxes for evidence of damage that may have occurred during transit.
BC29 B ATTERY ABINET 5. S YSTEM VERVIEW During normal operating conditions the UPS supplies power to the load as well as the necessary power required to keep the batteries at the proper float voltage. When AC power fails, the batteries will discharge in order to provide the necessary backup power to the load.
BC29 B ATTERY ABINET 6. S YSTEM PECIFICATIONS 6.1 B ATTERIES Please refer to system drawings for model specific information. Type: Valve Regulated Lead Acid (VRLA), sealed, non-spillable Voltage: 12 VDC Nominal Only cabinets with Flame Retardant Batteries are suitable for computer room use.
BC29 B ATTERY ABINET Wire Size and Type: Per NEC and/or all applicable national and local codes. Wire should be sized for a maximum voltage drop of 0.5 volt. 6.4 G ENERAL PECIFICATIONS Cabinet Size: 29.77”W x 29”D x 55.11”H Empty Cabinet Weight (approximately): 175 lbs.
BC29 B ATTERY ABINET 7. I NSTALLATION 7.1 P REPARATION 7.1.1 E QUIPMENT NSPECTION Remove the equipment from the packaging material and inspect for any shipping damage that may have been overlooked upon receipt of goods. Verify that the system includes all necessary hardware for installation.
BC29 B ATTERY ABINET 7.2 I NSTALLATION TEPS Before installing or maintaining this system, it is extremely important to read this manual and be sure that all system drawings and schematics are reviewed and clearly understood. If there are any questions concerning this manual or any of the installation or maintenance procedures and/or requirements please contact a C&C Power representative before proceeding.
BC29 B ATTERY ABINET 7.2.4 DC C ONNECTIONS Review the attached system drawings and schematics for model specific information on DC output connections. Wire should be sized for a maximum voltage drop of 0.5 volt. Battery cabinets that are not supplied with an incorporated DC output disconnect device must have an appropriate disconnect device provided external to the cabinet.
BC29 B ATTERY ABINET 8. S YSTEM AINTENANCE Before proceeding with system maintenance, be sure to review and understand all of the SAFETY PRECAUTIONS in this manual! Verify that the output breaker is in the off/open position before servicing the system.
BC29 B ATTERY ABINET 11. Reconnect any removed string jumpers and make sure the connections are properly torqued. 12. Check the battery string voltage at input side of the circuit breaker. 13. Reconnect the UPS to the battery string by turning on (closing) the circuit breaker in the battery cabinet.
BC29 B ATTERY ABINET 10. W ARRANTY LIMITED WARRANTY AND EXCLUSIONS C&C Power, Inc. strives to produce quality products at reasonable prices. If you are not satisfied with our product because of a defect, we will repair or replace the defective part or parts free of charge for a period of one year from the date of purchase.
C&C Power, Inc. ◦ 395 Mission Street ◦ Carol Stream, IL 60188 ◦ Phone: 630.617.9022 ◦ www.ccpower.com...