• This smoke alarm may be interconnected with as many as 11 addi- tional Firex model AD, ADC, PAD, FADC and FPAD smoke alarms, and/or as many as 6 Firex model ADH heat alarms for a total of not more than 18 interconnected devices.
7. If interconnection is desired, connect yellow wire from con- nector to interconnect wire between smoke alarms. See sec- tion INTERCONNECTING SMOKE ALARMS. NOTE: If this will be a single-station smoke alarm, cover yellow wire with electrical tape and tuck into junction box.
• This smoke alarm may be interconnected with as many as 11 additional Firex model AD, ADC, PAD, FADC, and FPAD smoke alarms, and/or as many as 6 Firex model ADH heat alarms for a total of not more than 18 interconnected devices. DO NOT con- nect to any type or model smoke alarm.
3. If smoke alarm does not sound, turn off power at main fuse box or circuit breaker and check wiring. Retest smoke alarm. REPLACE OR RETURN THE ALARM IF THE PUSH-TO-TEST FUNCTION DOES NOT OPERATE PROPERLY AFTER FOLLOWING THE PROCEDURES OUTLINED ABOVE (see REPAIR below).
Invensys Controls Americas warrants to the original consumer purchaser each new smoke alarm to be free from defects in material and workmanship under normal use and service for a period of five (5) years from the date of purchase. For Invensys Controls...