en | Safety
Object and Liquid entry – Never push objects of any kind into this apparatus through
openings as they may touch dangerous voltage points or short-out parts that could result in a
fire or electric shock. Never spill liquid of any kind on the apparatus.
25. Coax grounding – If an outside cable system is connected to the apparatus, be sure the
26. Protective grounding – An apparatus with class I construction shall be connected to a
Note for power connections
This label may appear on the bottom of the apparatus due to space limitations.
To reduce the risk of electrical shock, DO NOT open covers. Refer servicing to qualified
service personnel only.
To prevent fire or shock hazard, do not expose units to rain or moisture.
Installation should be performed by qualified service personnel only in accordance with the
National Electrical Code or applicable local codes.
Power disconnect: If the apparatus is mains powered and a power supply cord set is
provided, the disconnect device is the mains plug of the power cord set.
If an AC‑DC adapter is provided and the mains plug that is part of the direct plug‑in device,
the AC‑DC adapter is the disconnect device.
The socket outlet shall be near the apparatus and shall be easily accessible.
18-Jun-2015 | 04 | F01U306898
cable system is grounded. U.S.A. models only: Section 810 of the National Electrical
Code, ANSI/NFPA No.70-1981, provides information with respect to proper grounding of
the mount and supporting structure, grounding of the coax to a discharge apparatus, size
of grounding conductors, location of discharge unit, connection to grounding electrodes,
and requirements for the grounding electrode.
power outlet socket with a protective grounding connection.
Protective earthing – An apparatus with class I construction shall be connected to a
mains socket outlet with a protective earthing connection.
For permanently connected equipment, a readily operable mains plug or all-pole mains
switch shall be external to the equipment and in accordance with all applicable
For pluggable equipment, the socket-outlet shall be installed near the equipment and
shall be easily accessible.