For North America Installations
Detachable Power Supply Cord Not Provided. Power Supply Cord Selection (for units which power
supply cord not furnished with) - Use UL Listed detachable power supply cord, three conductors,
minimum 4.5 ft. (1.5m), maximum 14.8 ft. (4.5m) long. Types SP-2, SP-3, SV and similar cords may be
provided if the cord is not long. Refer to Tables 3 and 4 for details.
Type of cord
Ratings of cord
Liebert GXT4 models 700-1500VA and 2000VA have three groups of outlets as shown in Figures 2, 3
and 5. One group is always On; the other two groups may be controlled with either programmed
responses or over an SNMP network. The 3000VA GXT4 UPS has four groups of outlets: two groups
are not controlled (always On), and two groups may be controlled with either programmed responses
or over an SNMP network.
Verify that the equipment is plugged into the appropriate outlets if any outlets will be controlled with
1. Plug equipment into the appropriate output receptacles on the rear of the Liebert GXT4.
1. Do not overload any output receptacle.
2. Output cable length should not exceed 10m (32.8 ft).
2. Plug the input receptacle of the Liebert GXT4 into the input power connection.
3. Install the two cable strain relief fixtures to secure either the input or output cables to prevent
a. Insert one end into the provided holes on the rear of the unit.
b. Place the power cord(s) inside the loop.
Tighten the loop around the cables.
Figure 10 Cable strain relief
Hold the cable
Type of Cord
SVE, SVO, SVOO, SVT, SVTO, SVTOO, SPE-2, SPT-2, NISP-2,
NISPE-2, NISPT-2, SPE-3, SPT-3, SJ, SJE, SJO, SJOO, SJT,
SJTO, SJTOO, S, SE, SO, SOO, ST, STO, STOO
Minimum Wire Gauge
Minimum Cord Ratings
250 V, 105
250 V, 105
Insert into the provided hole
to secure the line buckle
Attachment Plug Ratings
20 A, +250V (NEMA L6-20P)
15 A, +250V (NEMA L6-15P)