4.19.3 Initial settings and specifications of RS-485 communication
(Pr. 117 to Pr. 124, Pr. 331 to Pr. 337, Pr. 341, Pr. 549)
Used to perform required settings for communication between the inverter and personal computer.
There are two different communications: communication using the PU connector of the inverter and
communication using the RS-485 terminals.
You can perform parameter setting, monitor, etc. from the PU connector or RS-485 terminals of the inverter
using the Mitsubishi inverter protocol (computer link communication).
To make communication between the personal computer and inverter, initialization of the communication
specifications must be made to the inverter.
Data communication cannot be made if the initial settings are not made or there is any setting error.
[PU connector communication related parameter]
PU communication station
PU communication speed
PU communication stop bit
PU communication parity
Number of PU
PU communication check
PU communication waiting
PU communication CR/LF
Communication operation and setting
0 to 31
48, 96, 192, 384
0 to 10
0.1 to 999.8s
0 to 150ms
Specify the inverter station number.
Set the inverter station numbers when two or
more inverters are connected to one
Set the communication speed.
The setting value × 100 equals the
For example, the communication speed is
19200bps when the setting value is "192".
Stop bit length
Without parity check
With odd parity check
With even parity check
Set the permissible number of retries at
occurrence of a data receive error. If the
number of consecutive errors exceeds the
permissible value, the inverter will come to
an alarm stop.
If a communication error occurs, the inverter
will not come to an alarm stop.
No PU connector communication
Set the interval of communication check time.
If a no-communication state persists for
longer than the permissible time, the inverter
will come to an alarm stop.
transmission to the inverter and response.
Set with communication data.