Wiring of the control circuit of the 75K or higher
For wiring of the control circuit of the 75K or higher, separate away from wiring of the main circuit.
Make cuts in rubber bush of the inverter side and lead wires.
(view from the inside)
Make cuts along the lines inside with
a cutter knife and such.
Mounting the operation panel (FR-DU07) on the enclosure surface
Having an operation panel on the enclosure surface is convenient. With a connection cable, you can mount the
operation panel (FR-DU07) to the enclosure surface, and connect it to the inverter.
Use the option FR-CB2
Securely insert one end of connection cable into the PU connector of the inverter and the other end into the
connection connector of the operation panel (FR-DU07) along the guides until the stoppers are fixed.
Do not connect the cable to a LAN port of a personal computer, to a fax modem socket, or to a telephone connector. Doing so may
damage the inverter and the connected device due to the differences in the electric specifications.
⋅ Refer to page 6 for removal method of the operation panel.
⋅ When using a commercially available connector and cable as a parameter unit connection cable, refer to Chapter 2 of
Instruction Manual (Applied).
⋅ The inverter can be connected to the computer and FR-PU04/FR-PU07.
, or the following connector and cable available on the market.
Parameter unit connection cable
Operation panel connection connector