4.26.3 Maintenance timer alarm (Pr. 503, Pr. 504)
When the cumulative energization time of the inverter reaches the parameter set time, the maintenance timer
output signal (Y95) is output.
This can be used as a guideline for the maintenance time of peripheral devices.
Maintenance timer alarm output
⋅ The cumulative energization time of the inverter is stored into the EEPROM every hour and indicated in Pr. 503
Maintenance timer in 100h increments. Pr. 503 is clamped at 9998 (999800h).
⋅ When the Pr. 503 value reaches the time set in Pr. 504 Maintenance timer alarm output set time (100h increments), the
maintenance timer alarm output signal (Y95) is output.
⋅ For the terminal used for the Y95 signal output, assign the function by setting "95" (positive logic) or "195" (negative
logic) to any of Pr. 190 to Pr. 196 (output terminal function selection).
⋅ The cumulative energization time is counted every hour. The energization time of less than 1h is not counted.
⋅ When terminal assignment is changed using Pr. 190 to Pr. 196 (output terminal function selection), the other functions may be
affected. Please make setting after confirming the function of each terminal.
♦ Parameters referred to ♦
Pr. 190 to Pr. 196(output terminal function selection)
(MT) is displayed on the operation panel (FR-DU07).
Refer to page 230
0 (1 to 9998)
0 to 9998
Set "0" in Pr.503
Display the cumulative energization time of
the inverter in 100h increments.
Writing the setting of "0" clears the
cumulative energization time.
Set the time taken until when the
maintenance timer alarm output signal
(Y95) is output.