Precautions on system
When connecting a GOT to the FUJI SYS temperature controller, set a terminating resistor for the
For the GOT, set a terminating resistor with the DIP switches of the RS-422/485 serial communication
Clock setting of GOT
The temperature controller does not have the clock function. Even though [Adjust] or [Broadcast] is set for
the clock setting, the setting is invalid (not processed).
Precautions on setup
FIX processing of temperature controller
Do not turn off the temperature controller during FIX processing. Doing so may damage the data stored in
a nonvolatile memory, resulting in the failure of the temperature controller.
Setting station No. of temperature controller
Make sure that the temperature controller corresponding to the station No. set for the host address exists
in the system configuration.
• For details of system configuration and
• For precautions and restrictions
• For outlined procedure and checking of FUJI SYS
temperature controller connection
• For controllers that can be monitored by GOT and
• For connection method with Handy GOT
For restrictions and precautions on controllers connected to a GOT, refer to the manual for each controller.
Chapter 33 in GOT1000 Series Connection Manual
Chapter 2 in GT Designer2 Version2 Screen Design
Manual (For GOT1000 Series) (SH-080530ENG)
Chapter 32 in Handy GOT User's Manual
4.6 Temperature Controller
4.6.5 FUJI SYS temperature controller