Precautions on system
When the programmable controller is a terminating station, do not connect a terminating resistor.
Set the GOT terminating resistor setting to off.
Communication may not be correctly executed in a system that has the programmable controllers
applicable to the PC3J extended function and those inapplicable to the function.
The system must have programmable controllers applicable to the PC3J extended function only or those
inapplicable to the function only.
Clock setting of GOT
The GOT clock setting is enabled only for the programmable controller corresponding to the station No.
set for the host address.
Setting station No. of programmable controller
Make sure that the programmable controller corresponding to the station No. set for the host address
exists in the system configuration.
The system alarm can be displayed only for the programmable controller set as the host address.
When connecting a GOT to the programmable controller compatible with the PC3J extended function,
only the system alarm of the program No.1 can be displayed.
Version of PC3J
For PC3J, use the version 2.1 or later.
• For details of system configuration and
• For precautions and restrictions
• For outlined procedure and checking for JTEKT
programmable controller connection
• For controllers that can be monitored by GOT and
• For connection method with Handy GOT
For restrictions and precautions on controllers connected to a GOT, refer to the manual for each controller.
4.3 Third Party Programmable Controller
4.3.6 JTEKT programmable controller
Chapter 15 in GOT1000 Series Connection Manual
Chapter 2 in GT Designer2 Version2 Screen Design
Manual (For GOT1000 Series) (SH-080530ENG)
Chapter 17 in Handy GOT User's Manual