Gas installation 12 kW
The installation must be performed by authorized
staff. Mount a manual shut-off valve prior to the
The gas pipe to the machine must be
dimensioned for a power output of 12 kW.
The machine is equipped with an allgas burner.
On delivery from the factory the machine is
adjusted to a nozzle pressure equivalent to the
calorific value indicated on the data sign.
Note! If you convert to another kind of gas a
corresponding sign enclosed must replace
the existing sign on the back of the machine.
Check that the nozzle pressure and the calorific
value correspond with the values indicated in the
table. If not, you must get in touch with the
Before connecting the machine the pipe must be
After connection all the connections must be
tested for leakage.
Test run 12 kW
Connect a pressure gauge to testsocket outlet
(1). (Page 11)
Select programme (Normal/perm.press)
Start the machine.
Check the nozzle pressure. See table page 11.
Any adjustment is carried out on the adjusting
screw (3) of the regulator under nipple (2).
Check that the gas flame burns steadily with
a bluish colour.
Having completed the test the machine is made
Installation GAS 200/270 litres