2.Removing the fan motor
(1)Remove the top panel(five screws),the service panel(four
screws),and the front panel (two screws).(See Photo 1.)
(2)Disconnect the fan motor connector.
(3)Remove the propeller.
(4)Remove the fan motor.
3.Removing the 4-way valve
(1)Remove the screws of the top panel , and remove it.(See
(2)Remove the service panel,rear panel,and connect cover
panel. Recover refrigerant gas.
(3)Remove the electrical parts.(See Photo 2.)
(4)Detach the brazed joint of 4-way valve and pipe.
(See Photo 4.)
4.Removing the linear expansion valve
(1)Remove the service panel.(See Photo 1.)
(Gas release is not required if the unit is pumped down.)
(2)Remove the coil of linear expansion valve.
(3)Detach the brazed joint of linear expansion valve and pipe.
4 way valve
R. V. coil