For more information about the possible redundant configuration status icon combinations, see
"Redundant UPS status (on page 94)."
The attached devices screen enables you to:
View attached devices and load segment power status
Control load segments
The estimated UPS runtime appears at the top of the screen. The total time required to shut down the
entire UPS is recalculated when attached devices are added, deleted, or modified. This time is determined
by the single largest time necessary to shut down a device attached to the UPS.
To add, delete, or configure attached devices, click Add New Device to display the Add / Edit Attached
Device screen (on page 69).
Controlling a load segment
To cycle the UPS, click Cycle in the Entire UPS section to gracefully shut down and turn on all load
To control an individual load segment, do one of the following in the section that corresponds to the load
segment you want to control:
Click Off to shut down a load segment, which allows for the graceful shutdown of attached devices.
Click On to turn on a load segment.
Click Cycle to gracefully shut down and turn on a load segment.
Add / Edit Attached Device screen
Click Add New Device on the Attached Devices screen. The Add Device screen appears.
("Controlling a load
Depending on the specific UPS model, this screen will vary.
segment" on page 69) (turn off, on, or cycle power)
HP UPS Management Module web interface 69