4. Dimensions and Required Servicing Space of Branch Box
PAC-AK31BC/PAC-AK32BC (3-branch type)
5. Refrigerant piping
* Always follow the specifications written in the installation manual of the outdoor unit. Exceeding these requirements may cause reduced performance of the
equipment, and malfunctions.
Suspension bolt: W3/8 (M10)
Refrigerant pipe flared connection
Drain hose size: O.D.0 (VP16)
4.1. Space required for installation and servicing
(1) Front View (Fig. 4-5)
On the side of piping
() Side View (Fig. 4-6, Fig. 4-7)
For indoor installations
*1: A minimum 350 mm is required for 90° bends in refrigerant piping.
When using the PAC-AK52BC/PAC-AK53BC branch box to connect P100
indoor unit(s), the following procedure is required.
1. Connect the Y-shaped connection pipe end(s) to the indoor unit(s).
2. Mount the branch box.
3. Connect the Y-shaped connection pipe ends to the branch box.
is " Min. 200 mm " <recommendation>.
(Premise: The slope of drain piping is securable 1/100 or more. Required
200 mm or more, when not securable.)
In the case of less than 00 mm (for example
of Branch box from a maintenance hole becomes difficult (Only exchange work
of a PCB, linear expansion valve coils, sensors and drain pan is possible).
600 mm " <recommendation>.
In the case of " 450", prepare a maintenance hole at a PCB side (as it is shown
in Fig. 4-7), and "Min. 300 mm" is needed as distance
In the case of less than 300 mm (for example
work of Branch box, linear expansion valve coils, sensors, and drain pan from a
maintenance hole becomes difficult (Only exchange work of a PCB is possible).
(3) Top View (Fig. 4-8)
When facing in the opposite direction to the refrigerant piping.
is 100 mm), the exchange work
is 100 mm), the exchange
To outdoor unit