3.2.6 SYSTEM READY LED
The System Ready LED (green) has two main pro-
poses. First, the LED will be ON when the
AUTO/OFF/MANUAL switch is in the AUTO position,
utility is present, and there are no system alarms.
This ON state indicates the system is fully ready for
The system ready LED will be OFF when the switch
is in the manual or OFF positions.
The system ready LED is also used to indicate the
presence of utility sensing at the PCB when the switch
is either in the AUTO or MANUAL modes. The LED
will flash at the rate of 1/2 second on, 1/2 second off
if the utility sensing level is below the transfer back
This secondary function is only available with dip
switch two in the OFF position (standard ATS appli-
MANUAL TRANSFER AND
To transfer electrical loads to the Standby (EMER-
GENCY) power source side and start the engine man-
ually, refer to the Owner's Manual of the particular
Engine speed governing is also controlled by the
engine control board. Connector J2 on the engine
control board interfaces with a governor driver mod-
ule and the Bosch throttle body. The engine governor
has been set by the factory during final testing of the
generator and, in most cases, should not be adjusted.
If, however, adjustments are necessary, or a new
engine control board is installed in the generator, the
following procedure should be followed (Figure 3.2):
1. Set all three potentiometers (pots) fully counter-
2. Under no load condition, increase the GAIN pot
as much as possible without causeing instability.
3. Apply 1/4, 1/2, 3/4 and full load to the unit.
Decrease the GAIN pot if there is instability at any
4. Under full load condition, increase the stability
pot until the unit returns to 60 Hertz (or 50 Hertz
in 50 Hertz applications).
5. Reduce load to 3/4, 1/2, 1/4 and no load.
Decrease the stability pot if there is instability at
any load point.
Power Systems, Inc.
Section 3 — Operation
QUIETSOURCE™ Liquid-cooled 30 kW Generators
6. Adjust differential pot to make the recovery to
load changes even faster and minimize load
change undershoot and overshoot. If it is set too
high it may introduce oscillations at some load. It
can be set to zero (full CCW) if a small amount
causes oscillations at some load.
Figure 3.2 — Engine Governor Adjustment
RETRANSFER AND SHUTDOWN
When utility power source voltage has been restored,
electrical loads may be transferred back to that
source and the generator can be shut down as follows:
• Verify that utility power supply voltage to the trans-
fer switch has been positively turned OFF, using
whatever means provided (such as utility main line
• Set the generator's main circuit breaker to its OFF
or OPEN position.
• Let the generator engine run at no-load for a few
minutes, to stabilize internal unit temperatures.
• On the generator console, set the AUTO/OFF/
MANUAL switch to OFF. Wait for engine to come to
a complete stop.
• For transfer to UTILITY position, refer to the
Owner's Manual of the particular transfer switch.
• Turn on the utility power supply to the transfer
switch, using whatever means provided (such as a
utility main line circuit breaker). The utility power
source now powers the loads.
ON = 50 HZ
ON = GTS
OFF = ATS (standard mode)
OFF = 60 HZ