To reset your system's smoke detectors and the keypad Memory of Alarm display (after heat
or smoke is no longer present):
First determine and correct the cause of the fire alarm condition (e.g., fan smoke from the
smoke detector chamber, reset the pull station, etc.) and then:
Press the control's SILENCE/RESET button again or re-enter your User
Code plus the [OFF] key at the keypad.
If your building has a fire sprinkler system, your installer may have installed a sensor that
monitors the sprinkler system (e.g., to determine whether the main water gate valve is open
or that there is adequate water pressure, etc.). Your system provides the following
indications when a supervisory condition is detected.
CALL YOUR INSTALLER IMMEDIATELY FOR SERVICE WHEN A
SUPERVISORY INDICATION APPEARS!
The control's buzzer and the keypad buzzer both produce a rapid on/off pulsing
The keypad LCD (Fixed-Word) displays the word "SUPV" and the number of the zone
with the supervisory condition. Alpha keypads also display a description of the zone.
A supervisory message is sent to the central station.
Silencing and Resetting a Supervisory Indication
To silence the control and keypad buzzers:
Press the control's SILENCE/RESET button or enter your User Code, +
the OFF key.
– 8 –