50063482-001 Bag assembly includes:
• 8-pin connector
NOTE: This equipment has been tested and found to
comply with the limits for a Class A digital
device, pursuant to part 15 of the FCC Rules.
These limits are designed to provide reasonable
protection against harmful interference when the
equipment is operated in a commercial environ-
ment. This equipment generates, uses and can
radiate radio frequency energy and, if not
installed and used in accordance with the
instruction manual, may cause harmful interfer-
ence to radio communications. Operation of this
equipment in a residential area is likely to cause
harmful interference in which case the user will
be required to correct the interference at his own
The Class A digital apparatus complies with
The OI Display contains software that incorporates many
features that are designed to guide you safely through the
commissioning process. Safety, however, is your
Read all documentation carefully and respond appropriately to
all error messages
PANEL HOLE CUTOUT SIZE FOR FRONT PANEL MOUNT: 8 (203) WIDE X 5-1/2 (140) HIGH.
PANEL HOLE CUTOUT SIZE FOR REAR PANEL MOUNT: 7-1/8 (181) WIDE X 4-11/16 (119) HIGH.
Fig. 1. S7999D OI Display dimensions in inches (mm).
• CR2032 coin battery
• Mounting hardware
• 3 clamp filters (1 for 24V power and 1 for each Modbus)
Improper configuration can cause fuel buildup and
Improper user operation may result in PROPERTY
LOSS, PHYSICAL INJURY or DEATH.
Using the OI Displays to change parameters, must be
attempted by only experienced and/or licensed
burner/boiler operators and mechanics.
The OI Display can be mounted on the door panel of an
1. Select the location on the door panel to mount the dis-
play; note that the device will extend into the enclosure
at least one inch past the mounting surface.
2. Provide an opening in the panel door 8" wide X 5 1/2"
high (for front panel mount) or 7 1/8" wide X 4 11/16"
high (for rear panel mount). See Fig. 1 or use cutout
templates provided in Fig. 98 and Fig. 99.
3. Place the OI Display in the opening and use it as a tem-
plate to mark the location of the four mounting screw
holes. Remove the device.