9.2 Refrigerant Charging
If the refrigerant charge is lost due to service or a
leak, a new charge must be accurately weighed in.
If any of the old charge is left in the system, it must
be recovered before weighing in the new charge.
Refer to the unit nameplate for the correct charge
weight and refrigerant type.
9.3 Compressor/Capacitor Replacement
This compressor is equipped with a two terminal
external overload and a run capacitor, but no start
capacitor or relay.
CAUTION-ELECTRICAL SHOCK HAZARD:
Electrical power must be present to perform
some tests. These tests should be performed
by a qualified service person.
For HVAC Installer Only • Installation Guide