Installation of the Controls
NSTALLATION OF THE
4- Connect the wires to the main control.
(See figure 17.)
5- Make sure the instruction pull-out is in the
occupant's language. If not, turn it to the other side.
(See figure 18.)
6- Reinstall the cover plate and the button(s).
7- Connect the wires to their corresponding position inside the
electrical compartment. Make sure the connections of the unit
and of the wall control correspond exactly. (See figure 19.)
8- Connect the optional control (if applicable) by referring to Section 8.3.
9- Do the appropriate connection to the furnace (if applicable) by referring to Section 8.4.
10- NOTE: If the unit is installed in a cold region (Zone A, as defined in Section 3.0), set up "extended
defrost" by removing jumper JU1F on the main circuit board inside the electrical compartment
(see Section 9.0).
11- Plug in the unit and do the "overall verification" of the system as described in Section 11.0.
Y R G B
F F I OC OL Y R G B