3 Installation Instructions
Connection of signal lines
Connect the signal lines of the pressure converters of the safety shut-off valve as
shown in figure 5.
See figure 2 (chapter 2.2), connection B, for connection to the pressure converter.
The signal lines of the pressure converters should have a minimum diameter of
10 mm. Sometimes it is desirable (and in certain countries obligatory) that the vent
opening (see figure 2 (chapter 2.2), connection D) of the diaphragm of the pressure
converter is installed to outside. In this way no gas can get into the installation space
when a diaphragm fractures. The vent pipeline should be no longer than 40 m.
Mind the following when mounting the HON HSV:
When there is a possibility that filth detach from the pipeline between dust filter and
safety valve, it is advisable to fit a simple wire-mesh filter right before the
HON HSV during the first operational period. This filter may be removed later;
Mount the safety shut-off device in such a way that the arrow on the valve body
points into the flow direction.
Figure 5: Example with two safety shut-off valves
Figure 6: Example of a safety shut-off valve in dual execution ("one-of-the-two" redundancy).
© 2017 Honeywell International Inc
Operation and maintenance manual HON HSV086