A Mounting on DIN rail
B Wall mounting
C Flush panel mounting
3.1 Mounting and installation
No further parts are needed.
With four ellipse screws for holes with diameter of
4 mm x 6 mm
With HVAC Products ARG462.10 mounting kit
Mounting instruction M 3351.1
Electronic injection valve (EIV)
Laboratory measurements reveal that control
performance improves when the valve is installed higher
than the evaporator (min. 5 cm)! This is especially
important with plate heat exchangers.
CE1U3372XX / H 74 319 0555 0 a