Dialer Capture Module Information
RED – Steady ON
RED – Flashing
GREEN – Steady ON
GREEN – Blinks every 2 sec.
GREEN – Blinks twice every sec.
GREEN – Blinks 10 times every sec.
LED Display Information
NOTE: If a wire pulled out of the LED Board Connector
refer to the diagram on right and reinsert wire, ensuring
the connector pin is locked in.
Messages exist in buffer.
No messages to be sent. Waiting for messages.
PowerBoost1 communication problem.
Connection with the Communicator is lost.
PowerBoost1 and Communicator connections are lost.
Yellow – ON when radio trouble is present.
• Both IP and Cell communication paths are lost.
• Communicator radio is not registered.
• Old Alarm Time has been exceeded. (Message has not been
delivered within the fixed 10-minute window.)
Buzzer – Upon loss of AC power, this will beep once every 10 sec-
Yellow – ON when battery is low (<11.5VDC).
Yellow – (not used)
Yellow – ON when no AC is present (< 90VAC).
Green – ON when AC is present.
NOTE: Telco ports 1 (primary dialer) and
2 (secondary dialer) may be used instead
of the terminal board.
Whichever connection method is used,
both Telco paths must be connected to
the Fire Panel.