The batteries can be internal or external, however, it is recommended to install
them where the UPS is capable of charging them. Please remember that, if the
battery is not charged for periods of over 2 – 3 months they can be subject to
The Fluxpower HE Three phase from 10 kVA to 20 kVA has internal batteries.
Servicing of batteries should be performed by qualified personnel only.
Replace the batteries with the same number of block and capacity.
Replace only with original type.
Caution: do not dispose of batteries in fire. The battery may explode.
Caution: do not open or mutilate batteries. Released electrolyte is harmful to
the skin and eyes. It may be toxic.
Caution: do not dump exhausted batteries in the environment.
4.3.1 BATTERY CONNECTION AND POSITIONING
After the battery installation, before closing BCB, check the battery voltage
on the BCB circuit breaker.
In case of not directly supplied cabling, please connect the cables to the
battery breaker (BCB) as shown in the Figure below.
Figure 7: Cabling of BCB fuse holder