❋ ❋ The mixing valve is controlled based on the FCU WL value .
❋ ❋ As the #4044 value increases and the #4045 value decreases, the control speed increases . (Temperature hunting may
occur if the control speed increases depending on the load . )
❋ ❋ The additional pump and mixing valve should be purchased separately . TW4 sensor is included in the product accessories .
❋ ❋ TW2 : Water temp . sensor 2
• When the thermostat control is set as 'Use' , the mixing valve can be used for Zone 1 and Zone 2 . (When both FSV
#2091 and #2092 are set as 1)
Connection of the mixing valve
2: Mixing Valve_CW
3: Mixing Valve_CCW
EHS MONO Kit-EU_IM_05388A-04_EN.indd 42
(Default, 15 m) CNS045(BLU)
2016-06-23 오후 3:43:11