Connecting a relay or a magnetic contactor for a backup heater (Not Directly connect a backup heater)
1 . Connect a "relay or a magnetic contactor" with "CNP003,CNP001,CNP002" .
f When a backup heater mode is "ON" at 1st step, a control signal of AC 230V goes through CNP003 and CNP001 .
f When a backup heater mode is "ON" at 2nd step, a control signal of AC 230V goes through CNP003 and CNP002 . .
This port can NOT supply enough power for driving a backup heater .
It's just for providing a ON/OFF control signal .
Maximum current is 0 . 5 A .
EHS MONO Kit-EU_IM_05388A-04_EN.indd 24
Relay or Magnetic Contactor Wire
2016-06-23 오후 3:43:03