Optimization of the Settings
(for hot water heating operating with temperature between
20 and 90 °C)
During the regulation procedure open the radiator valves
completely. (Set the thermostat valves at the maximum va -
If in the test room (room where the temperature sensor is
located) radiator valves are installed, these must be left
Close all windows and doors.
Proceed gradually by making only small changes.
Wait for the outcome of the change after each setting
(approx. 1 h).
Depending on the type of system – radiator/convector heating
(up to 90 °C), low temperature heating, air heating, mixing cham -
ber regulation – and depending on the layout of the heating surfa -
ces various flow or supply temperatures are needed to reach the
right room temperature – and hence also different settings on the