t-NEXT DF DX
POSSIBLE AIR INTAKE FOR OVER VERSIONS
OVER VERSION - AIR INTAKE FROM THE BOTTOM
Thanks to the particular basement design, it is possible to have the unit air intake from the bottom side.
With this solution, it is necessary to foresee the optional blind frontal panels
OVER VERSION - AIR INTAKE FROM THE BACK SIDE
(Sizes E4, E5, E6, E7, E8, E9 excluded)
It is possible to have the unit air intake from the back side.
Due to the limited size of the air intake, the air flow is limited to the 20% of the nominal one.
The air intake must be made by Customer during installation.
In case the air intake is used for fresh air, it is necessary the temperature / humidity probe reposition in
front of the heat exchanger, to allow for optimum reading of the values of temperature / humidity.
The electric cable of the probe has enough length for the repositioning.
AIR INTAKE FROM THE BACK SIDE
Max air flow
Back side view
E1 – E2 – E3