Communication detail settings
Make the settings according to the usage environment.
■1. GE (SNP-X)
If no setting is provided for the data length for the controller, set "8 bits".
If the setting is provided for the data length for the controller, set the same set value for the data length for the GOT as that for the
Set this item when change the transmission speed used for communication
with the connected equipment.
Set this item when change the data length used for communication with the
Specify the stop bit length for communications.
Specify whether or not to perform a parity check, and how it is performed
Set the number of retries to be performed when a communication error
Set the time period for a communication to time out.
Specify the host address (station No. of the GOT to which the PLC is
connected) in the connected network.
Set this item to adjust the transmission timing of the communication request
from the GOT. (Default: 5ms)
(1) Communication interface setting by the Utility
The communication interface setting can be changed on the Utility's [Communication setting]
after writing [Communication Settings] of project data.
For details on the Utility, refer to the following manual.
GOT2000 Series User's Manual (Utility)
(2) Precedence in communication settings
When settings are made by GT Designer3 or the Utility, the latest setting is effective.
11.4 GOT Side Settings
0 to 5times
1 to 30sec
00 to 31
0 to 300ms
11 - 13