Device Range that Can Be Set
The device ranges of controller that can be used for GOT are as follows.
Note that the device ranges in the following tables are the maximum values that can be set in GT Designer3.
The device specifications of controllers may differ depending on the models, even though belonging to the same series.
Please make the setting according to the specifications of the controller actually used.
When a non-existent device or a device number outside the range is set, other objects with correct device settings may not
■1. Setting item
Set the device name, device number, and bit number.
The bit number can be set only when specifying the bit of word device.
Displays the device type and setting range which are selected in [Device].
Set the monitor target of the set device.
The following shows the relation between station numbers of the temperature controller and the GOT data register.
RKC SR Mini HG
The bit specification of the word device
To monitor the temperature controller of the specified station No.
1 to 99:To monitor the temperature controller of the specified station No.
100 to 115To specify the station No. of the temperature controller to be monitored by the value of GOT data
Device settings of RKC temperature controller
Set by a value of "unit address + 1".
• For unit address 0: Set "1".
• For unit address F: Set "16".
GOT data register (GD)
Setting range of each word device
..0000 to ..FFFF
9.6 Device Range that Can Be Set
1 to 99
(If setting a value outside the range above,
a device range error occurs.)
9 - 73