Device Range that Can Be Set
The device ranges of controller that can be used for GOT are as follows.
Note that the device ranges in the following tables are the maximum values that can be set in GT Designer3.
The device specifications of controllers may differ depending on the models, even though belonging to the same series.
Please make the setting according to the specifications of the controller actually used.
When a non-existent device or a device number outside the range is set, other objects with correct device settings may not
■1. Setting item
8 - 42
8.6 Device Range that Can Be Set
Set the device name, device number, and bit number.
The bit number can be set only when specifying the bit of word device.
Set the CPU No. (1, 2) of the device to be monitored.
When device B is selected, the CPU No. is fixed to 1.
Displays the device setting range which are selected in [Device].
Set the monitor target of the set device.
Select this item when writing data to all the temperature controllers connected.
When bit specification of word device is performed, data are written to the temperature controller of the
station No. set for [Host Address] of the communication detail settings.
Monitoring and writing with bit specification of word device are performed only for the station No. set for [Host
(When writing the data in numerical input, the data is written to the connected temperature controller other
than the ones specified by the word device during input, and the temperature controller set for [Host
Address] is monitored during other than input (displaying).)
Select this item when monitoring the temperature controller of the specified station No.
After selecting, set the station No. in the following range.
1 to 99:To monitor the temperature controller of the specified station No.
100 to 115:To specify the station No. of the temperature controller to be monitored by the value of GOT data
The following shows the relation between station numbers of the temperature controller and the GOT data register.
When there is no setting for the CPU No. in the communication settings on the temperature controller side, set the CPU No. on
the GOT side to (1) (default).
GOT data register (GD)
1 to 99
(If setting a value outside the range above,
a device range error occurs.)