Station number setting
Set each station number so that no station number overlaps.
The station number can be set without regard to the cable connection order. There is no problem even if station numbers
are not consecutive.
■1. Direct specification
When setting the device, specify the station number of the temperature controller of which data is to be changed.
■2. Indirect specification
When setting the device, indirectly specify the station number of the inverter of which data is to be changed using the
16-bit GOT internal data register (GD10 to GD25).
When specifying the station No. from 200 to 215 on GT Designer3, the value of GD10 to GD25 compatible to the
station No. specification will be the station No. of the temperature controller.
Specification station NO.
5 - 32
5.5 Temperature Controller Side Setting
Examples of station number setting
Specifying a station No. between 200 and 215
(Example of specifying the station No. 215)
Set the station No. to "200".
Input "215" to the internal device GD10.
The station No. 215 is specified.
For details, refer to (2) Indirect specification shown below.
1 to 199
216 to 255
1 to 255
For the setting other than the above, error
(dedicated device is out of range) will occur.