■2. Communication detail settings
Make the settings according to the usage environment.
GOT Net No.
GOT Communication Port No.
Set different values for [GOT Station] of [Detail Setting] and [Station] of [Connected Ethernet Controller Setting].
When assigning the same driver to the multiple channels, in the communication drivers set as the second and following, the
default value of [GOT Communication Port No.] becomes the earliest number in the vacant numbers of No. 6000 and later.
Set the network No. of the GOT.
Set the station No. of the GOT.
Set the GOT port No. for the connection with the Ethernet module.
Set the number of retries to be performed when a communication timeout
When receiving no response after retries, the communication times out.
Specify the time period from the GOT startup until GOT starts the
communication with the PLC CPU.
Set the time period for a communication to time out.
Set the delay time for reducing the load of the network/destination PLC.
Connected Ethernet Controller Setting
(1) Communication interface setting by the Utility
The communication interface setting can be changed on the Utility's [Communication setting]
after writing [Communication Settings] of project data.
For details on the Utility, refer to the following manual.
GOT2000 Series User's Manual (Utility)
(2) Precedence in communication settings
When settings are made by GT Designer3 or the Utility, the latest setting is effective.
4.3 Ethernet Connection
1 to 239
1 to 254
1024 to 5010, 5014 to 65534
(Except for 5011, 5012, 5013 and
49153 to 4917)
0 to 5times
3 to 255sec
1 to 90sec
0 to 10000(ms)
4 - 33