(For FUJI MICREX-SX SPH)
Leave the setting as default. If the set value is changed, communication with the PLC is disabled.
(1) Host address
When connecting to PLC by RS-232 communication, set the Host Address to "0".
(2) Communication interface setting by the Utility
The communication interface setting can be changed on the Utility's [Communication
Settings] after writing [Communication Settings] of project data.
For details on the Utility, refer to the following manual.
(3) Precedence in communication settings
When settings are made by GT Designer3 or the Utility, the latest setting is effective.
Set this item when change the transmission speed used for communication
with the connected equipment. (Default: 38400bps)
Set this item when change the data length used for communication with the
Specify the stop bit length for communications. (Default: 1bit)
Specify whether or not to perform a parity check, and how it is performed
Set the number of retries to be performed when a communication error
occurs. (Default: 3time)
Set the time period for a communication to time out.
Set this item to adjust the transmission timing of the communication request
from the GOT. (Default: 0ms)
GOT2000 Series User's Manual (Utility)
0 to 5times
1 to 30sec
0 to 300ms
4.2 Serial connection
4 - 21