Fire mode (Control panel: Menu PAR
Drive ignores all commands from keypad, fieldbus and PC tool and preset
frequency when activated. If activated, alarm sign is shown on the keypad
and warranty is void.
In order to enable the function, you need to set a password in the descrip-
tion field for parameter Fire Mode password. Please note, the NC (normally
closed) type of this input!
Fire mode password
Fire mode frequency select
Application manual HVAC232/402 | Document 27-652 | Issue ENG06 | 2019-08-07
Table 38. Fire mode.
THE WARRANTY IS VOID IF THIS FUNCTION IS ACTIVATED!
There is also a different password for test mode to be used for
testing the Fire Mode without warranty becoming void.
1234 = Test mode
1001 = Enable
1515 = Disable
0 = Fire mode preset
1 = Preset speed 0
2 = Keypad
3 = Fieldbus
4 = AI1
5 = AI2
6 = PID
7 = AI+AI2
8 = Motor potentiometer
9 = AIE1
10 = Temperature input 1
11 = Temperature input 2
12 = Temperature input 3
NOTE! This parameter will be locked when password for
fire mode is activated (not in the test mode), and not
only when fire mode input is set. To change the
parameter you have to disable fire mode.