• Separate the wiring of the control circuit away from the wiring of the main circuit.
Make cuts in rubber bush of the inverter side and lead the wires through.
(viewed from inside)
Make cuts along the lines on
the inside with a cutter knife
When using separate power supplies for the
control circuit and the main circuit
Cable size for the control circuit power supply (terminals R1/L11 and S1/
• Terminal screw size: M4
• Cable gauge: 0.75 to 2 mm
• Tightening torque: 1.5 N·m
If a fault occurs and the electromagnetic contactor (MC) installed at the inverter's input line is opened, power supply to the
control circuit is also stopped and the fault signals cannot be output anymore. Terminals R1/L11 and S1/L21 of the control
circuit are provided to keep outputting the fault signals in such a case. Follow the following steps to wire terminals R1/L11 and
S1/L21 on the inverter to the power input lines of the MC.
Terminals R1/L11 and S1/L21 are connected to terminals P/+ and N/- with a jumper respectively. Do not connect the power
cable to incorrect terminals. Doing so may damage the inverter.
Remove the jumper
2. INSTALLATION AND WIRING
2.6 Control circuit