Cabinet air conditioning
The minimum dimensions listed below for ventilation clearances must be observed. No other
components or cables must be located in these areas.
Device failure caused by overloading of devices and components
If the guidelines for installing SINAMICS G130 equipment are not observed, this can
significantly reduce the service life of the components and result in premature device and
• Observe the guidelines for installing the devices and components.
You must take into account the following specifications when using SINAMICS G130:
● Ventilation clearance
● Wiring and cabling
● Air guidance
Table 5- 1
Ventilation clearances for the components
The clearances refer to the area around the ventilation slots on the front cover.
Notes on the dimensions
The dimensions refer to the outer edges of the devices.
A dimension drawing is available in the Operating Instructions.
Cabinet design and EMC
Operating Instructions, 07/2016, A5E00427629A