Explanation of the Operation Panel
The operation panel cannot be removed from the inverter.
(a) Unit indicator
(b) Monitor (4-digit LED)
(c) Setting dial
(d) Start command
(e) MODE key
(f) SET key
Hz: Lit to indicate frequency. (Flickers when the set frequency monitor is displayed.)
A: Lit to indicate current.
(Both "Hz" and "A" turns OFF to indicate a value other than frequency or current. )
Shows the frequency, parameter number, etc.
(To monitor the output power, the set frequency and other items, set Pr. 52.)
The dial of the Mitsubishi inverters. The setting dial is used to change the frequency and
Press the setting dial to perform the following operations:
To display a control method (general-purpose motor control or IPM motor control) during the
To display the set frequency when pressed for 1s or longer under PU operation mode or External/
PU combined operation mode (Pr. 79 = "3")
To display the present setting during calibration
To display a fault history number in the faults history mode
Select the rotation direction in Pr. 40.
Used to switch among different setting modes.
Holding this key for 2 seconds locks the operation. The key lock is invalid when Pr. 161 = "0
Used to enter a setting.
If pressed during the operation,
monitored item changes as the
Lit or flickers during inverter operation.
* Lit: When the forward rotation operation is being performed.
Slow flickering (1.4s cycle): When the reverse rotation operation is being performed.
Fast flickering (0.2s cycle): When
When the frequency command is less than the starting frequency.
When the MRS signal is being input.
Lit to indicate the parameter setting mode.
Monitor indicator Lit to indicate the monitor mode.
PU: Lit to indicate the PU operation mode.
EXT: Lit to indicate the External operation mode.(EXT is lit at power-ON in the initial setting.)
NET: Lit to indicate the Network operation mode.
PU and EXT: Lit to indicate EXT/PU combined operation mode 1 and 2
All of these indicators are OFF when the command source is not at the operation panel.
Used to stop operation commands.
Used to reset a fault when the protective function (fault) is activated.
Used to switch between the PU and External operation modes.
To use the External operation mode (operation using a separately connected frequency setting
potentiometer and start signal), press this key to light up the EXT indicator.
operation mode. )
PU: PU operation mode
EXT: External operation mode
Used to cancel the PU stop also.
simultaneously changes the operation mode.
has been pressed or the start command has been
given, but the operation cannot be made.
simultaneously (0.5s), or change the Pr .79 setting to change to the combined
(g) Operation status indicator
(h) Parameter setting mode indicator
(i) Monitor indicator
(j) Operation mode indicator
(k) STOP/RESET key
(l) PU/EXT key
Energy saving monitor is displayed when the
energy saving monitor is set with Pr. 52.