Unless the existing network is in MELSECNET mode or MELSECNET ΙΙ mode and only the first half is set, the
network parameter settings need to be changed.
If the second half of settings have been made in the MELSECNET ΙΙ mode or MELSECNET ΙΙ composite
mode, the B and W station send range must be reset, and the station's inherent parameters must be set, etc.
Furthermore, when AnNCPUs, AnACPUs or AnSCPUs are part of the system, the program should be modified
because station inherent parameters cannot be set.
For precautions regarding the existing MELSECNET(ΙΙ) system configuration, refer to "Transition from
MELSEC-A/QnA (Large Type), AnS/QnAS (Small Type) Series to Q Series Handbook (Network Modules)".
Transitional step 2
Artisan Technology Group - Quality Instrumentation ... Guaranteed | (888) 88-SOURCE | www.artisantg.com
4.1 Replace MELSECNET(ΙΙ) with MELSECNET/10