A sufficient level of vacuum is necessary for
proper performance of the vacuum interrupters.
Although vacuum leaks are rare, the vacuum
integrity should be checked periodically.
voltage of the contact gap and internal vacuum
interrupter pressure has been found to be
interrupter integrity is checked by performing a
high potential test across the open gap of the
Toshiba offers a compact vacuum checker (Type
CI35-1D) which enables a quick and easy check
Alternatively, any commercially available AC high
potential tester may be used which is capable of
delivering at least 25 milliamperes at 22 kV for a
period of one minute.
Applying abnormally high voltage across a pair of
contacts in vacuum may produce X-rays. The
radiation may increase with the increase in
voltage and/or decrease in contact spacing. X-
recommended voltage and normal contact
spacing is extremely low and well below the
maximum permitted by standards.
additional safety measure, however, it is
recommended that all personnel keep at least 1
meter (3.3 ft) away from the vacuum circuit
breaker while this test is performed.
Radiation exposure hazard.
X-rays may cause illness or
injury. Stay at least 1 meter
(3.3 ft) away from the circuit
breaker during the vacuum
check test .
Buy: www.ValinOnline.com | Phone 844-385-3099 | Email: CustomerService@valin.com
Hazardous voltages are
present during dielectric
testing which can result in
severe injury or death.
Only qualified personnel
should conduct this testing.
1. The circuit breaker should be disconnected
from the main circuit and be in the OFF
2. Connect all the line side primary terminals
together and to the output of the vacuum
checker or AC hi-pot machine. Connect all
the load side primary terminals together and
to the ground terminal of the vacuum checker
or AC hi-pot machine.
3. Increase the voltage from zero to 22kV AC at
a rate of approximately 2kV per second.
Hold the voltage at this value for 1 minute
and observe the current drawn by the
4. Decrease the voltage back to zero.
Fig. 33 Toshiba Portable Vacuum Checker