User Manual SICLOCK GPS1000
shows a diagram of the connection from GPS1000 to SICLOCK TS with lightning protection module 2XV9450-
1AR83. The parts illustrated in photo and the grey cable are included under the scope of delivery for the complete package
SICLOCK GPS1000 with the exception of the lightning protection module). The red and green cables must be made avail-
able on site.
The lightning protection module should be installed in the building as near as possible to where the cable coming from the
antenna enters the building.
It is absolutely essential that the earth cable shown in green and connected to the DIN rail (cross section 25 sq. mm or more)
is connected in the shortest possible way and as straight as possible to a foundation earth.
Fig 5: Installation diagram for SICLOCK TS with lightning protection module.
Order numberr 2XV9450-1AR82-BA