The physical link between the PROFIBUS interface and the PROFIBUS network is via a
floating RS-485 interface that is part of the module. Depending on the network configuration,
data rates of 9.6 Kbps up to a maximum of 12 Mbps are possible in the PROFIBUS network.
You will find information about the structure of a PROFIBUS network in the system manual
"PROFIBUS Network Manual". The document is part of the Manual Collection. You will also
find this on the Product Support pages under the following entry ID:
The D-sub female connector has the following pin assignment:
Operating Instructions, 02/2018, C79000-G8976-C283-05
Socket pin 1 is not connected.
Socket pin 2 is not connected. With other MPI/DP components,
the return line of the floating 24 V power supply may be via this
Signal line B of the PROFIBUS connector.
RTSAS, input signal for direct MPI link. The control signal is "1"
active when the automation system connected over a special
MPI cable is sending.
M5EXT return line (GND) of the 5 V power supply and refer-
ence potential for the signals RTSAS and RTS of the
P5EXT power supply (+5 V) for the 5 V power supply.
(only for bus termination)
Socket pin 7 is not connected. With other MPI/DP components,
the P24V supply of the floating 24 V power supply may be via
Signal line A of the PROFIBUS connector.
Description of the device
1.2 PROFIBUS interface